Eaton's Power factor correction:
a guide for the plant engineer states,
Capacitors and transformers can create dangerous resonance
conditions when capacitor banks are installed at the service
entrance. Under these conditions, harmonics produced by
nonlinear devices can be amplified manyfold.
Problematic amplification of harmonics becomes more likely as
more kVAR is added to a system that contains a significant amount
of nonlinear load.
You can estimate the resonant harmonic by using this formula:
\$ h = \sqrt {\frac {kVA_{sys}}{kVAR}} \$
kVAsys = shortcircuit capacity of the system
kVAR = amount of capacitor kVAR on the line
h = the harmonic number referred to a 60 Hz base
If h is near the values of the major harmonics generated by a
nonlinear device—for example, 3, 5, 7, 11—then the resonance
circuit will greatly increase harmonic distortion.
Two questions:

Why would resonance depend on the shortcircuit capacity of the system? (Can you explain the formula?)

I can't find a similar equation for 50 Hz. Any suggestions?
For reference, this is for a 1 MVA transformer (shortcircuit capacity not known at this time) and 350 kVAr PF bank).
Best Answer
The formula is derived from the basic formula for a simple resonant circuit;
\$f_0 = \frac{1}{2 \pi\sqrt{LC}}\$
L and C are calculated from the short circuit impedance and the capacitor bank impedance. The short circuit impedance is assumed to be purely inductive. That assumption is justified by the assumption that the transformer X/R ratio is 5 for threephase distribution transformers smaller than 150 kVA and progressively higher for larger transformers. X/R is assumed to be 8 for a typical 1 MVA transformer. Since the capacitor and transformer impedances are based on the relevant power frequency, that frequency is the fundamental for the harmonic order calculation. On other words, the formula is valid for either 50 or 60 Hz as long as the capacitor bank VAR rating and the short circuit VA are stated or calculated based on the frequency of interest.
The formula is given in IEEE Std 5191992. I found the assumptions and derivation in seminar notes printed for a 1990 seminar.