I am looking into a series of 2 pole circuit breakers (Sprecher + schuh 's series KTU7 UL489 molded case circuit breakers) and they seems to have 2 ratings, a thermal trip rating and a magnetic trip rating. What is the difference between these two ratings? Is the magnetic trip rating the same as the instantaneous trip rating?

# Fixed thermal Trip vs fixed magnetic trip current ratings

powerprotection

###### Related Topic

- Electronic – Short circuit protection for high current wearable: fuse, polyswitch, TBU, circuit breaker, something else
- Electronic – Transformer VA Ratings, Power factor, and Pulsed current
- Electronic – Difference between instantaneous, definite time and inverse time over current protection relays
- Electronic – Full Load Amps vs General Purpose Amps
- Electronic – Fuses & current ratings – are there fuses that blow “fast” close to their nominal rating
- Electronic – How to determine whether a switch can handle the power/current in a circuit

## Best Answer

The thermal setting is a

thermal overloadprotection. It has a time-delayed response. The heavier the overload, the faster it trips. It may be implemented by something like a bimetallic strip.The magnetic setting is

instantaneous short-circuit protection. It has no intentional delay. It may be implemented by something like a solenoid plunger, restrained by a spring.Here is an illustration of a typical time-current curve for a miniature circuit breaker (Clipsal 4 series) showing the thermal and magnetic trip characteristics. Note the thermal trip takes a long time - minutes or seconds - while the magnetic trip responds in 10ms or less.